BS5467 CU/XLPE/PVC/AWA/PVC 0,6/1,0 kV 1-conductor 50-120 + 1000 mm² Removed
The cable may be used for fixed installation indoors and outdoors in air and ground.
CU/XLPE/PVC/AWA/PVC is a XLPE insulted, PVC bedded, aluminium wirearmoured and PVC sheathed cable with circular annealed copperconductors complying with BS EN 60228 class 2. The cable is designed according to BS 5467. The armour is a single layer of aluminiumwires, laid in a left hand direction. The core has harmonized colour and is covered with an extruded layer of polymeric compound.The external surface on the outer sheath is embossed "NEXANS GS ELECTRIC CABLE 600/1000V BS 5467 "H" NUMBER OF CORES X NOMINAL AREA OF THE CONDUCTOR XLPE YEAR OF MANUFACTURE" + meter marking. The cable meets the requirements for flammability stated in IEC60332-1, BS EN 50265-2-1.
The current ratings are thoroughly presented in ERA 69-30 partV: «CURRENT RATING STANDARD FOR DISTRIBUTION CABLES».
The cable is manufactured and tested according to BS 5467 in appl. parts.
Quality and environmental management system
Certified according to ISO 9001, IRIS, ISO/TS 16949 and ISO 14001.
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Short-circuit max. conductor temperature||250°C|
|Bending factor when installed||6(xD)|
|See all products|