BS5467 Multi-core Booklet Armoured CU/XLPE/PVC/SWA 0,6/1,0 kV 5-37 cores - Auxiliary cables Removed
The cable may be used for fixed installation indoors and outdoors in air and ground.
CU/XLPE/PVC/SWA/PVC is a XLPE insulated, PVC bedded, steel wire armoured and PVC sheathed auxiliary cable with circular, compacted and stranded annealed copper conductors complying with BS EN 60228 class 2. The cable is designed according to BS 5467. The armour is a single layer of galvanized steel wires, laid in a left hand direction. The cores are marked with numbers and they are laid up in concentric layers and covered with an extruded layer of pvc compound. The external surface on the outer sheath is embossed "NEXANS GS BASEC ELECTRIC CABLE 600/1000 V BS 5467 NUMBER OF CORES X NOMINAL AREA OF THE CONDUCTOR XLPE YAER OF MANUFACTURE" + metre marking.
The cable can be loaded according to IEC 60287: "CALCULATION OF THE CONTIOUS CURRENT RATING OF CABLES (100% LOAD FACTOR)".
The cable is manufactured and tested according to BS 5467.
Quality and environmental management system
Certified according to ISO 9001, IRIS, ISO/TS 16949 and ISO 14001.
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Minimum installation temperature||0°C|
|Maximum operating temperature||90°C|
|Short-circuit max. conductor temperature||250°C|
|Bending factor when laying||6(xD)|
|Flame retardant||IEC 60332-1|
|See all products|